Main range of productCanalis range compatibilityCanalis KTCanalis KS offer typeStandard product or component typeTap-off unit busbar trunking compatibilityCanalis KS busbar trunking with plug-in outletsCanalis KT busbar trunking with KS type plug-in outlets [Ie] rated operational current250 A at 35 °C protection typeCircuit breaker : NSX250 provided equipmentCircuit breaker to be ordered separately mounting modePlug-in with fixed polarity tap-off unit polarity3L+N+PE colourWhite RAL 9001 Complementary device applicationMedium power distribution [Ue] rated operational voltage230...690 V depending on protective device [Uimp] rated impulse withstand voltage6.8 kV [Ui] rated insulation voltage400 V depending on protective device500 V depending on protective device690 V depending on protective device network frequency50/60 Hz control typeRotary handle electrical connectionCrimp lug - ISO40 - cable : 150 mm² flexibleCrimp lug - ISO40 - cable : 150 mm² rigid door/cover opening sideRight tap-off unit disconnection modeBy rotary operating handle number of openings1 opening for FL21 gland plate standardsIEC 61439-1IEC 61439-6 width532 mm depth300 mm depth (door open)726.5 mm height432 mm product weight12.5 kg Environment earthing systemTTITTN-S IP degree of protectionIP55 conforming to IEC 60529 IK degree of protectionIK08 conforming to IEC 62262 Offer Sustainability Sustainable offer statusGreen Premium product RoHS (date code: YYWW) REACh Product environmental profile Product end of life instructionsNeed no specific recycling operations Contractual warranty Warranty period18 months 18 months
Documents and DownloadsLanguage
CatalogueSizeAdd to My DocumentsCADSizeAdd to My DocumentsCanalis - KSB - Tap-off unit - 250A (Version 1.0)DVD Canalis KB-KN-KS-KT-KR_3D CAD simplified (Version 3.0)CAD files for KSB250DC4: TAP-OFF UNIT 250 A COMPACT (Version 1.0)CertificateSizeAdd to My DocumentsInstruction sheetSizeAdd to My DocumentsProduct Environmental ProfileSizeAdd to My Documents
No results found.Unfortunately, related FAQs are unavailable due to temporary technical issues. Please try again later.